R410A and R22
refrigerant difference and brass difference in where?
A lot of friend said it is difficult to distinguish between.
Come down and we know about the differences between them, be sure to remember!
10 different 1, R410A of R22 and R410A belongs to low toxicity, no combustion propagation, R22 non-combustible also;
Does not destroy the ozone layer 2, R410A and R22 is fatal for the ozone layer destruction;
3, than R22, R410A system the total heat transfer characteristics of heat transfer efficiency is high, the heat exchanger can be miniaturized;
4, R410A system refrigeration
capacity better, R22 was 100%, 147% R410A;
5, R410A for HFC -
And HFC -
125 mixture refrigerant;
6 work pressure is higher than R22, R410A 50 ~ 70%, about 1.
7 is larger than that of R22, R410A vapor density is big, so R410A steam flow rate compared with R22 slow about 30%;
8 is more soluble than R22, R410A.
When particles floating in R410A, can smoothly circulate in the system;
Higher request of the copper tube, 9, R410A and R22 can use ordinary brass;
10, R410A fatal problem: can produce greenhouse gases, the effect of greenhouse gases produced by the even greater than the R22.
Therefore, R410A and not air-conditioning final environmental protection refrigerants solutions in China.
Copper tube R22 copper tube and R410A difference and note 1, R410A brass must use high strength compressive special brass.
Spare parts must also use dedicated.
R410a copper tube can be used in place of the ordinary R22 brass, but absolutely can't use regular R22 pipe to replace R410a;
2, new refrigerant R410A fission when installed, shall not be used and R22 air conditioning connecting pipe and confused refrigerant;
3, R410A air-conditioner installed high requirements.
Action quickly, emptying should fully, do not connect the sweat drip into the tube, don't put other insoluble impurities into the system, is best done in sunny day;
4, maintenance, if cut the refrigeration system, it is necessary to change the filter drier, and time of the refrigeration system is exposed to the air shall not be more than five minutes.
5, after the maintenance of pumping air into vacuum state, the use of vacuum pump should be special vacuum pump, may not cause refrigerant mixture of pollution, and must ensure that the vacuum time in more than 25 minutes.
6, R410A refrigerant should be stored in under 30 ° C environment, if the above 30 ° C, in the environment must be under 30 ° C environment for more than 24 hours before using.
Using our Arkool to differentiate our content, services and consumer products, we seek to develop the most creative, innovative and profitable entertainment experiences and related products in the world.
Hangzhou E cool refrigeration Co.,Ltd will become the destination store for customers, offering the convenience of multiple brands and channels, and providing a personal high touch shopping experience that helps create lifelong customer relationships.
give you an additional start capacitor suppliers
option for your start capacitor suppliers, whether it being a start capacitor suppliers, start capacitor suppliers or start capacitor suppliers. Go and get more info at Arkool Refrigeration.
Hangzhou E cool refrigeration Co.,Ltd sells start capacitor suppliers and yet their focus on operational excellence and mastery of distributed manufacturing facilities start capacitor suppliers has made them the dominant player in the space.
Like anything else in start capacitor suppliers, there are a variety of choices and types to choose from, and each of them will affect your budget in some form. Hangzhou E cool refrigeration Co.,Ltd offers a range of quality at competitive prices.