About filling refrigerant, is gas or liquid, must have all already know, many of the Lao shifu often see someone consulting the refrigerant filling, exactly on the gas?
To summarize, here for you easy reference.
1, the three concepts refrigerants, non azeotropic mixed refrigerants and single working medium azeotropic refrigerants, refrigerant: single working medium refrigerant components only a working medium;
Non azeotropic refrigerants: two or more different refrigerant mixture to a certain percentage of the refrigerants, it in saturated state, the composition of gas liquid two phase composition;
Azeotropic refrigerants: there are two or more different refrigerant mixture to a certain percentage of the azeotrope, this kind of refrigerant under certain pressure can keep certain evaporating temperature and the composition of gas liquid two phase keep ratio unchanged.
2, liquid or gas?
Whether gaseous or liquid refrigerant, single working medium inside composition will not change, so the filling refrigerant can filling gas.
, azeotropic refrigerants although composition is different, but the boiling point is the same, so the composition of gas and liquid two same, so you can filling gas;
, non azeotropic refrigerants due to the boiling point is different, so the liquid refrigerant and gas refrigerant composition is not the same, actually as if gas, will inevitably lead to add refrigerant components, such as only added a gaseous refrigerant, so can only add the density of its liquid.
4, why not add liquid all see here a lot of friend, whisper in my heart, since to distinguish so difficult, I don't care what is added liquid refrigerants, as guaranteed not to can?
In general, as we all know, refrigerant charging finally is need to add the device runs after, and from the compressor suction mouth 気 added;
If liquid refrigerant, equivalent to the compressor suction 気 mouth into the liquid refrigerant, obviously cause compressor liquid impact;
Damage to the compressor.
5, summarize common refrigerant liquid or gaseous state said so much, a lot of friend to see not bottom go to, here is directly collect all common refrigerant liquid or gaseous, maintenance for everybody reference.
And gaseous refrigerant: R13, everything, R22
, R23, R290, R32, R500, R600a 2)
, add liquid refrigerant: R401A, R410B, R407C, R410A
So much of the refrigerant, believe friend also can not remember clearly chu.
A word to tell you the secret: as long as it is at the beginning of R4 * liquid refrigerant is added, the remaining gas. air conditioner capacitor
are all following the most compatible manufacturing regulations.
If you are ready to stop the problem of start capacitor suppliers
and go back to normal, contact us at Arkool Refrigeration. Hangzhou E cool refrigeration Co.,Ltd is ready to help you out.
Based on the refrigerant gas
, here are the top compliance challenges businesses face, and what you can do to make them easier on ourselves.
Hangzhou E cool refrigeration Co.,Ltd provides innovative technology and prompts our customers to know the development of our producing air conditioner capacitor.
Utilizing high technology to manufacture products can afford a fully experience to customers by using refrigerant gas.