Generally by observing the evaporation pressure, evaporation temperature and frost situation to judge the suction of throttle valve refrigerant flow.
Throttle valve block is the important factors influencing the refrigerant flow, main cause of throttle valve block of ice wall and dirty wall.
Technicians believe ice wall is due to the poor effect of drying dryer, moisture is contained in refrigerant, flowing through the throttle valve, the temperature fell to below 0 ℃, refrigerant water in the ice and jam throttle hole;
Dirty plugging was due to the throttle valve import filter net accumulation of more dirt, refrigerant circulation, plug formation.
System of refrigeration
dose is insufficient, lack of refrigeration capacity enough refrigerant cycle for two reasons, one is the refrigerant filling quantity is not enough, at this point, just add enough cold storage refrigerants.
Another reason is that the system refrigerant leakage is more, in this kind of situation, should first find funnelled, focusing on the pipes, valves, joints, found to leak after repairing, filling the plenty of refrigerants.
Refrigerator compressor efficiency is low, the capacity can not meet the requirement of the cold storage warehouse load compressor due to long-term operation, such as piston ring and cylinder parts due to wear serious, fit clearance increases, the sealing performance will be reduced, decreases in the coefficient of the gas compressor refrigerating capacity will be reduced.
When the heat load capacity is less than warehouse, will cause the warehouse temperature drop slowly.
By observing the compressor suction, exhaust pressure approximately determining the compressor refrigeration capacity.
If the compressor refrigeration capacity fell, the commonly used method is to replace the compressor cylinder, piston ring and if still cannot work, after replacement should consider other factors, even machine maintenance, troubleshooting. refrigerant gas
is not something to be ignored or taken for granted. It is there to keep your start capacitor suppliers comfortable year round. To find a cost effective solution, turn to Hangzhou E cool refrigeration Co.,Ltd.
If you want to know more about finding the proper for start capacitor suppliers
solutions, visit Arkool Refrigeration.
Visit Arkool Refrigeration to find recent dynamics of air conditioner capacitor and contact Hangzhou E cool refrigeration Co.,Ltd for the latest and most capable in global market.